In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.
This ground fault circuit interrupter wiring diagram of the same device leaves the switch out of the protected circuit. With this arrangement the receptacle is protected but the switch remains outside the circuit. This arrangement can be used to control a light or other device where the extra protection of a gfci is not necessary.
Here one ground fault circuit interrupter protects multiple duplex receptacles coming after it, known as multiple-location protection. Two-wire cable runs from the gfci to all the following receptacles. The line terminals on the gfci are connected to the circuit source and the load terminals are connected with a pigtail splice to each of the following receptacles. This keeps each duplex connected directly to the gfci.
In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.