This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
This diagram is similar to the one above, but with the electrical source originating at the fixture. Three-wire cable runs from there to the controllers. The neutral wire from the source is spliced directly to the white wire on the fan/light. The hot source wire is spliced to the white on the 3-wire cable and then spliced to the input wires on both controllers at the other end.
Splice both the fan and the light hot wires together with the common wire from the SW2. The traveler wires are spliced together in the ceiling fixture box. To control the fan and light separately, a builtin switch such as a pull chain or remote control is required on the fan/light.