This page contains wiring diagrams for ground fault circuit interrupter (gfci) receptacles. Included are diagrams for multiple gfci’s, a protected standard duplex receptacle, and a protected light fixture. Wiring for a switch and gfci receptacle in the same box is also shown to protect the switch and light or to protect other receptacles in the circuit. To wire a gfci circuit breaker see this link and wire a gfci switch combo at this link.
In these cases, it should be wrapped with electrical tape to mark it as hot. The ground wires will be green and/or bare copper. The ground should be spliced with a short piece of wire and connected to each device and outlet box that has a grounding terminal. In these drawing the brass colored terminal represent the hot side of the device and the silver colored terminal represent the neutral. Ground wires and terminals are in green.
This is the updated wiring for this arrangement, with a 2-wire cable added between the fan/light and switches. The white wire is no longer used for hot and the source neutral is run through to the switch box to satisfy the 2011 NEC requirement of a neutral wire in all switch boxes. All other wiring is the same as above.
The hot wire to the fan in a fan/light kit will usually be black and the light wire will be blue. The white wire is usually the neutral which is always connected directly to the source neutral, either at the source or through a splice in the switch box. The white wire may also be used to carry current when necessary.