This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
In this diagram, a light switch and receptacle are wired in the same box. Both devices are spliced to the same hot source and the neutral to the neutral on the receptacle, and through to the light fixture located in a separate box.
The source hot is spliced to the red wire which is connected to the bottom terminals on the switch at the other end. The black wire is connected to the top terminal on the switch which runs power back to the fan where it is spliced to both the black and blue fan wires.
In this diagram, two receptacle outlets are wired in the same box with a separate 120 volt source feeding each. Three-wire cable runs into the box. The black and red wires are hot and each is connected to one of the receptacles. The white, neutral wire is splice to each outlet so they share the return path. This is appropriate for standard duplex receptacles, but should not be used for GFCI receptacles. GFCI’s must have dedicated neutral connections to work properly.