This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
This page contains wiring diagrams for a ground fault circuit interrupter (gfci) with a built in switch. This device can be used to protect a garbage disposal and provide a gfci protected receptacle in a single gang outlet box. The switch can be included in the protected circuit or it can be used to control an unprotected light or other fixture.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
Run the cable through the clamp and tighten it down. Splice the cable wires to the fan wires using a pigtail splice and a wire nut. Connect the ground to the grounding terminal in the connection box and the ground wire from the fan, if there is one.
This diagram illustrates the wiring for a Cooper gfci/switch combo device wired to protect a garbage disposal. With this arrangement a receptacle, switch and disposal are protected with the ground fault breaker built into the device.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
To wire a 3-way switch circuit that controls both the fan and the light, use this diagram. As with all 3-way circuits, the common on one switch is connected to the hot source wire from the circuit. The common on the second 3-way switch is connected to the hot wires on the fan/light.
Splice both the fan and the light hot wires together with the common wire from the SW2. The traveler wires are spliced together in the ceiling fixture box. To control the fan and light separately, a builtin switch such as a pull chain or remote control is required on the fan/light.