This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.
Here two receptacles in one box are wired using the device terminals. With this arrangement, if receptacle #1 fails, receptacle #2 may also fail if failure is due to physical damage. However, if the copper tab conductors between the terminals remain intact, even if #1 stops functioning, receptacle #2 will probably still work.
In these cases, it should be wrapped with electrical tape to mark it as hot. The ground wires will be green and/or bare copper. The ground should be spliced with a short piece of wire and connected to each device and outlet box that has a grounding terminal. In these drawing the brass colored terminal represent the hot side of the device and the silver colored terminal represent the neutral. Ground wires and terminals are in green.
In this wiring, a switch and receptacle are in the same box and the switch controls the power to the outlet. The hot wire connects to the bottom terminal on the switch and the top output goes to the receptacle hot terminal. The neutral wire from the source connects directly to the receptacle neutral.