In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.
This diagram illustrates the wiring for a circuit with gfci receptacles followed by an unprotected light and switch. The light switch is connected directly to the source and the load terminals on the gfci are not used.