This diagram illustrates the wiring for a circuit with gfci receptacles followed by an unprotected light and switch. The light switch is connected directly to the source and the load terminals on the gfci are not used.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.
In this diagram, two receptacle outlets are wired in the same box with a separate 120 volt source feeding each. Three-wire cable runs into the box. The black and red wires are hot and each is connected to one of the receptacles. The white, neutral wire is splice to each outlet so they share the return path. This is appropriate for standard duplex receptacles, but should not be used for GFCI receptacles. GFCI’s must have dedicated neutral connections to work properly.