Here the exhaust fan is controlled by a timer instead of a switch. There should be two hot wires and a ground coming out of the timer casing, splice one of these to the hot source. Spice the second to the black, cable wire running to the fan. Splice the source neutral to the white cable wire and the ground to the ground wires. At the fan splice the wires, matching the colors of each.
This page contains wiring diagrams for a ground fault circuit interrupter (gfci) with a built in switch. This device can be used to protect a garbage disposal and provide a gfci protected receptacle in a single gang outlet box. The switch can be included in the protected circuit or it can be used to control an unprotected light or other fixture.
This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.
This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.
Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.
Here a gfci receptacle is added at the end of a row of duplex receptacles for single-location protection. The first outlet is connected to the source and 2-wire cable runs from box to box. All wires are spliced with a pigtail at the devices to pass current from one to the next. The load terminals on the gfci are not used and it does not protect the other receptacles in the circuit.
This wiring arrangement allows for lowering the lights with a dimmer and controlling the fan with the builtin pull chain. The source is at the ceiling outlet box and 3-wire cable runs from there to the switch box. The neutral from the source is spliced directly to the white wire on the fan kit and the cable, running it through to the switch box.
In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.