Here a gfci receptacle is added at the end of a row of duplex receptacles for single-location protection. The first outlet is connected to the source and 2-wire cable runs from box to box. All wires are spliced with a pigtail at the devices to pass current from one to the next. The load terminals on the gfci are not used and it does not protect the other receptacles in the circuit.
Run the cable through the clamp and tighten it down. Splice the cable wires to the fan wires using a pigtail splice and a wire nut. Connect the ground to the grounding terminal in the connection box and the ground wire from the fan, if there is one.
This is the updated wiring for this arrangement, with a 2-wire cable added between the fan/light and switches. The white wire is no longer used for hot and the source neutral is run through to the switch box to satisfy the 2011 NEC requirement of a neutral wire in all switch boxes. All other wiring is the same as above.
In this diagram wall outlets are wired in a row using the terminal screws to pass voltage from one receptacle to the next. In this diagram, multiple receptacles are connected together using the device, instead of a pigtail splice as shown in the next diagram. Using this method, any break or malfunction at one outlet will likely cause all outlets that follow to fail as well.