In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.
This is the updated wiring for this arrangement, with a 2-wire cable added between the fan/light and switches. The white wire is no longer used for hot and the source neutral is run through to the switch box to satisfy the 2011 NEC requirement of a neutral wire in all switch boxes. All other wiring is the same as above.
This diagram is similar to the one above, but with the electrical source originating at the fixture. Three-wire cable runs from there to the controllers. The neutral wire from the source is spliced directly to the white wire on the fan/light. The hot source wire is spliced to the white on the 3-wire cable and then spliced to the input wires on both controllers at the other end.
Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.