This page contains wiring diagrams for a ground fault circuit interrupter (gfci) with a built in switch. This device can be used to protect a garbage disposal and provide a gfci protected receptacle in a single gang outlet box. The switch can be included in the protected circuit or it can be used to control an unprotected light or other fixture.
Here two receptacles in one box are wired using the device terminals. With this arrangement, if receptacle #1 fails, receptacle #2 may also fail if failure is due to physical damage. However, if the copper tab conductors between the terminals remain intact, even if #1 stops functioning, receptacle #2 will probably still work.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.