This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.
This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
This diagram is similar to the one above, but with the electrical source originating at the fixture. Three-wire cable runs from there to the controllers. The neutral wire from the source is spliced directly to the white wire on the fan/light. The hot source wire is spliced to the white on the 3-wire cable and then spliced to the input wires on both controllers at the other end.
This ground fault circuit interrupter wiring diagram of the same device leaves the switch out of the protected circuit. With this arrangement the receptacle is protected but the switch remains outside the circuit. This arrangement can be used to control a light or other device where the extra protection of a gfci is not necessary.