This page contains wiring diagrams for ground fault circuit interrupter (gfci) receptacles. Included are diagrams for multiple gfci’s, a protected standard duplex receptacle, and a protected light fixture. Wiring for a switch and gfci receptacle in the same box is also shown to protect the switch and light or to protect other receptacles in the circuit. To wire a gfci circuit breaker see this link and wire a gfci switch combo at this link.
This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.
This wiring arrangement allows for lowering the lights with a dimmer and controlling the fan with the builtin pull chain. The source is at the ceiling outlet box and 3-wire cable runs from there to the switch box. The neutral from the source is spliced directly to the white wire on the fan kit and the cable, running it through to the switch box.
In this arrangement a light fixture and exhaust fan are wired to the same source. The light is controlled with a single-pole switch and the fan controlled with a timer as in the previous drawing. The hot source is spliced to each controlling device and the output of the controllers are connected as in the previous diagrams on this page.
The black cable wire is connected to the top terminal on the switch and spliced to the black and blue wires at the fan at the other end. The neutral source and ground are spliced through to the white and ground connections at the fan.
Here a gfci receptacle is added at the end of a row of duplex receptacles for single-location protection. The first outlet is connected to the source and 2-wire cable runs from box to box. All wires are spliced with a pigtail at the devices to pass current from one to the next. The load terminals on the gfci are not used and it does not protect the other receptacles in the circuit.
The white wire is wrapped with black tape to identify it as hot. The black wire connects the fan to the speed controller. The red wire connects the light to the dimmer.
This diagram shows two switches in the same box with two separate 120 volt sources. Three-wire cable is supplying the source for both switches with the black and red wires going to the bottom switch terminals. The black wire from each light is connected to the top terminal of their respective switch. The white and ground wires are spliced to run to each light fixture.