In this diagram wall outlets are wired in a row using the terminal screws to pass voltage from one receptacle to the next. In this diagram, multiple receptacles are connected together using the device, instead of a pigtail splice as shown in the next diagram. Using this method, any break or malfunction at one outlet will likely cause all outlets that follow to fail as well.
In this diagram, two receptacle outlets are wired in the same box with a separate 120 volt source feeding each. Three-wire cable runs into the box. The black and red wires are hot and each is connected to one of the receptacles. The white, neutral wire is splice to each outlet so they share the return path. This is appropriate for standard duplex receptacles, but should not be used for GFCI receptacles. GFCI’s must have dedicated neutral connections to work properly.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
This wiring arrangement allows for lowering the lights with a dimmer and controlling the fan with the builtin pull chain. The source is at the ceiling outlet box and 3-wire cable runs from there to the switch box. The neutral from the source is spliced directly to the white wire on the fan kit and the cable, running it through to the switch box.
In this arrangement a light fixture and exhaust fan are wired to the same source. The light is controlled with a single-pole switch and the fan controlled with a timer as in the previous drawing. The hot source is spliced to each controlling device and the output of the controllers are connected as in the previous diagrams on this page.
This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.