To wire a 3-way switch circuit that controls both the fan and the light, use this diagram. As with all 3-way circuits, the common on one switch is connected to the hot source wire from the circuit. The common on the second 3-way switch is connected to the hot wires on the fan/light.
Run the cable through the clamp and tighten it down. Splice the cable wires to the fan wires using a pigtail splice and a wire nut. Connect the ground to the grounding terminal in the connection box and the ground wire from the fan, if there is one.
Here the source is at the fan/light and a switch loop runs to the wall switch. The source is wired directly to the fan and spliced through to the switch. With this arrangement the light is controlled with the switch and the fan is hardwired for pull-chain control.
In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.