This page contains several diagrams for 2 or more receptacle outlets in one circuit. Wiring for multiple ground fault circuit interrupters (gfci) and standard duplex receptacles are included with protected and non-protected arrangements.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.
In this diagram, two receptacle outlets are wired in the same box with a separate 120 volt source feeding each. Three-wire cable runs into the box. The black and red wires are hot and each is connected to one of the receptacles. The white, neutral wire is splice to each outlet so they share the return path. This is appropriate for standard duplex receptacles, but should not be used for GFCI receptacles. GFCI’s must have dedicated neutral connections to work properly.
Run the cable through the clamp and tighten it down. Splice the cable wires to the fan wires using a pigtail splice and a wire nut. Connect the ground to the grounding terminal in the connection box and the ground wire from the fan, if there is one.
The source hot is spliced to the red wire which is connected to the bottom terminals on the switch at the other end. The black wire is connected to the top terminal on the switch which runs power back to the fan where it is spliced to both the black and blue fan wires.