Here the source is at the fan/light and a switch loop runs to the wall switch. The source is wired directly to the fan and spliced through to the switch. With this arrangement the light is controlled with the switch and the fan is hardwired for pull-chain control.
The black cable wire is connected to the top terminal on the switch and spliced to the black and blue wires at the fan at the other end. The neutral source and ground are spliced through to the white and ground connections at the fan.
Here two receptacles in one box are wired using the device terminals. With this arrangement, if receptacle #1 fails, receptacle #2 may also fail if failure is due to physical damage. However, if the copper tab conductors between the terminals remain intact, even if #1 stops functioning, receptacle #2 will probably still work.
This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.