Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.
Here GFCI’s are wired to a double-pole circuit breaker with the source split to provide 120 volts to two sets of receptacles. The neutral from the source is shared by both sets. Single-location protection is provided by each receptacle.
Here one ground fault circuit interrupter protects multiple duplex receptacles coming after it, known as multiple-location protection. Two-wire cable runs from the gfci to all the following receptacles. The line terminals on the gfci are connected to the circuit source and the load terminals are connected with a pigtail splice to each of the following receptacles. This keeps each duplex connected directly to the gfci.
This diagram shows two switches in the same box with two separate 120 volt sources. Three-wire cable is supplying the source for both switches with the black and red wires going to the bottom switch terminals. The black wire from each light is connected to the top terminal of their respective switch. The white and ground wires are spliced to run to each light fixture.