This page contains wiring diagrams for ground fault circuit interrupter (gfci) receptacles. Included are diagrams for multiple gfci’s, a protected standard duplex receptacle, and a protected light fixture. Wiring for a switch and gfci receptacle in the same box is also shown to protect the switch and light or to protect other receptacles in the circuit. To wire a gfci circuit breaker see this link and wire a gfci switch combo at this link.
Here the exhaust fan is controlled by a timer instead of a switch. There should be two hot wires and a ground coming out of the timer casing, splice one of these to the hot source. Spice the second to the black, cable wire running to the fan. Splice the source neutral to the white cable wire and the ground to the ground wires. At the fan splice the wires, matching the colors of each.
Here one ground fault circuit interrupter protects multiple duplex receptacles coming after it, known as multiple-location protection. Two-wire cable runs from the gfci to all the following receptacles. The line terminals on the gfci are connected to the circuit source and the load terminals are connected with a pigtail splice to each of the following receptacles. This keeps each duplex connected directly to the gfci.
This wiring arrangement allows for lowering the lights with a dimmer and controlling the fan with the builtin pull chain. The source is at the ceiling outlet box and 3-wire cable runs from there to the switch box. The neutral from the source is spliced directly to the white wire on the fan kit and the cable, running it through to the switch box.