This is the updated wiring for this arrangement, with a 2-wire cable added between the fan/light and switches. The white wire is no longer used for hot and the source neutral is run through to the switch box to satisfy the 2011 NEC requirement of a neutral wire in all switch boxes. All other wiring is the same as above.
In these cases, it should be wrapped with electrical tape to mark it as hot. The ground wires will be green and/or bare copper. The ground should be spliced with a short piece of wire and connected to each device and outlet box that has a grounding terminal. In these drawing the brass colored terminal represent the hot side of the device and the silver colored terminal represent the neutral. Ground wires and terminals are in green.
This diagram shows the wiring for multiple receptacles in an arrangement that connects each individually to the source. All wires are spliced to a pigtail which is connected to each device. This wiring allows for voltage at each device independent of the other outlets in the circuit.
This diagram illustrates the wiring for a Cooper gfci/switch combo device wired to protect a garbage disposal. With this arrangement a receptacle, switch and disposal are protected with the ground fault breaker built into the device.
This diagram illustrates the wiring for a circuit with gfci receptacles followed by a light and switch. By connecting the switch to the load terminals on the gfci, the light is protected against ground faults as well.
This page contains wiring diagrams for a ground fault circuit interrupter (gfci) with a built in switch. This device can be used to protect a garbage disposal and provide a gfci protected receptacle in a single gang outlet box. The switch can be included in the protected circuit or it can be used to control an unprotected light or other fixture.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
This wiring diagram illustrates the connections for dual controls, a speed controller for the fan and a dimmer for the lights. The source is at the controllers and the input of each is spliced to the black source wire with a pigtail. From the controllers, 3-wire cable runs to the ceiling outlet box.