Here one ground fault circuit interrupter protects multiple duplex receptacles coming after it, known as multiple-location protection. Two-wire cable runs from the gfci to all the following receptacles. The line terminals on the gfci are connected to the circuit source and the load terminals are connected with a pigtail splice to each of the following receptacles. This keeps each duplex connected directly to the gfci.
In this diagram, a light switch and receptacle are wired in the same box. Both devices are spliced to the same hot source and the neutral to the neutral on the receptacle, and through to the light fixture located in a separate box.
This wiring arrangement allows for lowering the lights with a dimmer and controlling the fan with the builtin pull chain. The source is at the ceiling outlet box and 3-wire cable runs from there to the switch box. The neutral from the source is spliced directly to the white wire on the fan kit and the cable, running it through to the switch box.
In this wiring, a switch and receptacle are in the same box and the switch controls the power to the outlet. The hot wire connects to the bottom terminal on the switch and the top output goes to the receptacle hot terminal. The neutral wire from the source connects directly to the receptacle neutral.
This page contains wiring diagrams for ground fault circuit interrupter (gfci) receptacles. Included are diagrams for multiple gfci’s, a protected standard duplex receptacle, and a protected light fixture. Wiring for a switch and gfci receptacle in the same box is also shown to protect the switch and light or to protect other receptacles in the circuit. To wire a gfci circuit breaker see this link and wire a gfci switch combo at this link.
This ground fault circuit interrupter wiring diagram of the same device leaves the switch out of the protected circuit. With this arrangement the receptacle is protected but the switch remains outside the circuit. This arrangement can be used to control a light or other device where the extra protection of a gfci is not necessary.
Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.
This diagram illustrates a switch and receptacle in the same outlet box located in the middle of the circuit. This wiring allows the electricity to continue from the receptacle, on to any other outlets in the circuit and it provides a switch to control a light fixture or other load, such as another receptacle or a fan.