This ground fault circuit interrupter wiring diagram of the same device leaves the switch out of the protected circuit. With this arrangement the receptacle is protected but the switch remains outside the circuit. This arrangement can be used to control a light or other device where the extra protection of a gfci is not necessary.
In this diagram, two receptacle outlets are wired in the same box with a separate 120 volt source feeding each. Three-wire cable runs into the box. The black and red wires are hot and each is connected to one of the receptacles. The white, neutral wire is splice to each outlet so they share the return path. This is appropriate for standard duplex receptacles, but should not be used for GFCI receptacles. GFCI’s must have dedicated neutral connections to work properly.
In these cases, it should be wrapped with electrical tape to mark it as hot. The ground wires will be green and/or bare copper. The ground should be spliced with a short piece of wire and connected to each device and outlet box that has a grounding terminal. In these drawing the brass colored terminal represent the hot side of the device and the silver colored terminal represent the neutral. Ground wires and terminals are in green.
Splice both the fan and the light hot wires together with the common wire from the SW2. The traveler wires are spliced together in the ceiling fixture box. To control the fan and light separately, a builtin switch such as a pull chain or remote control is required on the fan/light.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
The hot source is spliced to the black, fan wire and the black wire running to the dimmer. At the other end, the black cable wire is spliced to one of the hot dimmer wires, it doesn’t matter which one. The other dimmer wire is spliced to the red wire in the switch box which is spliced to the blue, light wire at the other end.
The hot wire to the fan in a fan/light kit will usually be black and the light wire will be blue. The white wire is usually the neutral which is always connected directly to the source neutral, either at the source or through a splice in the switch box. The white wire may also be used to carry current when necessary.
In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.
The source hot is spliced to the red wire which is connected to the bottom terminals on the switch at the other end. The black wire is connected to the top terminal on the switch which runs power back to the fan where it is spliced to both the black and blue fan wires.
Here one ground fault circuit interrupter protects multiple duplex receptacles coming after it, known as multiple-location protection. Two-wire cable runs from the gfci to all the following receptacles. The line terminals on the gfci are connected to the circuit source and the load terminals are connected with a pigtail splice to each of the following receptacles. This keeps each duplex connected directly to the gfci.
Run the cable through the clamp and tighten it down. Splice the cable wires to the fan wires using a pigtail splice and a wire nut. Connect the ground to the grounding terminal in the connection box and the ground wire from the fan, if there is one.