This diagram illustrates the wiring for a circuit with gfci receptacles followed by an unprotected light and switch. The light switch is connected directly to the source and the load terminals on the gfci are not used.
In this wiring, a switch and receptacle are in the same box and the switch controls the power to the outlet. The hot wire connects to the bottom terminal on the switch and the top output goes to the receptacle hot terminal. The neutral wire from the source connects directly to the receptacle neutral.
Splice both the fan and the light hot wires together with the common wire from the SW2. The traveler wires are spliced together in the ceiling fixture box. To control the fan and light separately, a builtin switch such as a pull chain or remote control is required on the fan/light.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.
This diagram is similar to the one above, but with the electrical source originating at the fixture. Three-wire cable runs from there to the controllers. The neutral wire from the source is spliced directly to the white wire on the fan/light. The hot source wire is spliced to the white on the 3-wire cable and then spliced to the input wires on both controllers at the other end.
Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.
In this diagram, a light switch and receptacle are wired in the same box. Both devices are spliced to the same hot source and the neutral to the neutral on the receptacle, and through to the light fixture located in a separate box.
This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
To wire an exhaust fan to a wall switch, use this diagram. These fans usually come with a small electrical connection box welded to the side of the housing. There will be a cover on the connection box that fastens with a small screw. Open it, pop the plug out of one of the wire holes and thread a wire clamp into it.
In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.