This diagram illustrates the wiring for a circuit with gfci receptacles followed by an unprotected light and switch. The light switch is connected directly to the source and the load terminals on the gfci are not used.
This ground fault circuit interrupter wiring diagram of the same device leaves the switch out of the protected circuit. With this arrangement the receptacle is protected but the switch remains outside the circuit. This arrangement can be used to control a light or other device where the extra protection of a gfci is not necessary.
Here GFCI’s are wired to a double-pole circuit breaker with the source split to provide 120 volts to two sets of receptacles. The neutral from the source is shared by both sets. Single-location protection is provided by each receptacle.
This page contains several diagrams for 2 or more receptacle outlets in one circuit. Wiring for multiple ground fault circuit interrupters (gfci) and standard duplex receptacles are included with protected and non-protected arrangements.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
Here the source is at the fan/light and a switch loop runs to the wall switch. The source is wired directly to the fan and spliced through to the switch. With this arrangement the light is controlled with the switch and the fan is hardwired for pull-chain control.
In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.
To wire a 3-way switch circuit that controls both the fan and the light, use this diagram. As with all 3-way circuits, the common on one switch is connected to the hot source wire from the circuit. The common on the second 3-way switch is connected to the hot wires on the fan/light.
This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
The source hot is spliced to the red wire which is connected to the bottom terminals on the switch at the other end. The black wire is connected to the top terminal on the switch which runs power back to the fan where it is spliced to both the black and blue fan wires.
Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.
The hot wire to the fan in a fan/light kit will usually be black and the light wire will be blue. The white wire is usually the neutral which is always connected directly to the source neutral, either at the source or through a splice in the switch box. The white wire may also be used to carry current when necessary.
This diagram shows the wiring for multiple receptacles in an arrangement that connects each individually to the source. All wires are spliced to a pigtail which is connected to each device. This wiring allows for voltage at each device independent of the other outlets in the circuit.