The black cable wire is connected to the top terminal on the switch and spliced to the black and blue wires at the fan at the other end. The neutral source and ground are spliced through to the white and ground connections at the fan.
This diagram shows the wiring for multiple receptacles in an arrangement that connects each individually to the source. All wires are spliced to a pigtail which is connected to each device. This wiring allows for voltage at each device independent of the other outlets in the circuit.
This diagram illustrates the wiring for a circuit with gfci receptacles followed by a light and switch. By connecting the switch to the load terminals on the gfci, the light is protected against ground faults as well.
This page contains wiring diagrams for a ground fault circuit interrupter (gfci) with a built in switch. This device can be used to protect a garbage disposal and provide a gfci protected receptacle in a single gang outlet box. The switch can be included in the protected circuit or it can be used to control an unprotected light or other fixture.
Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.
Here GFCI’s are wired to a double-pole circuit breaker with the source split to provide 120 volts to two sets of receptacles. The neutral from the source is shared by both sets. Single-location protection is provided by each receptacle.
This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.
In this wiring, the source is at the switch and 3-wire cable runs from there to the fan/light. The switch controls the light and the source is spliced through to the fan. With this arrangement, the fan is controlled by a pull-chain on the motor housing and the light is controlled with the switch. The neutral and ground wires are also spliced through to the fan/light.
In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.
In this diagram, a light switch and receptacle are wired in the same box. Both devices are spliced to the same hot source and the neutral to the neutral on the receptacle, and through to the light fixture located in a separate box.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
This is the updated wiring for this arrangement, with a 2-wire cable added between the fan/light and switches. The white wire is no longer used for hot and the source neutral is run through to the switch box to satisfy the 2011 NEC requirement of a neutral wire in all switch boxes. All other wiring is the same as above.
This diagram illustrates a switch and receptacle in the same outlet box located in the middle of the circuit. This wiring allows the electricity to continue from the receptacle, on to any other outlets in the circuit and it provides a switch to control a light fixture or other load, such as another receptacle or a fan.