In this diagram wall outlets are wired in a row using the terminal screws to pass voltage from one receptacle to the next. In this diagram, multiple receptacles are connected together using the device, instead of a pigtail splice as shown in the next diagram. Using this method, any break or malfunction at one outlet will likely cause all outlets that follow to fail as well.
The black cable wire is connected to the top terminal on the switch and spliced to the black and blue wires at the fan at the other end. The neutral source and ground are spliced through to the white and ground connections at the fan.
In this arrangement with 2 switches in one box, the bottom terminals are connected to pigtails spliced to the source. The top switch terminals connect to the black wires running to the light fixtures. The source neutral and ground wires are spliced to run to each light box.
To wire an exhaust fan to a wall switch, use this diagram. These fans usually come with a small electrical connection box welded to the side of the housing. There will be a cover on the connection box that fastens with a small screw. Open it, pop the plug out of one of the wire holes and thread a wire clamp into it.
This diagram illustrates the wiring for a Cooper gfci/switch combo device wired to protect a garbage disposal. With this arrangement a receptacle, switch and disposal are protected with the ground fault breaker built into the device.
Here GFCI’s are wired to a double-pole circuit breaker with the source split to provide 120 volts to two sets of receptacles. The neutral from the source is shared by both sets. Single-location protection is provided by each receptacle.
Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.
Here a gfci receptacle is added at the end of a row of duplex receptacles for single-location protection. The first outlet is connected to the source and 2-wire cable runs from box to box. All wires are spliced with a pigtail at the devices to pass current from one to the next. The load terminals on the gfci are not used and it does not protect the other receptacles in the circuit.
This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
This diagram is similar to the one above, but with the electrical source originating at the fixture. Three-wire cable runs from there to the controllers. The neutral wire from the source is spliced directly to the white wire on the fan/light. The hot source wire is spliced to the white on the 3-wire cable and then spliced to the input wires on both controllers at the other end.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
Here the exhaust fan is controlled by a timer instead of a switch. There should be two hot wires and a ground coming out of the timer casing, splice one of these to the hot source. Spice the second to the black, cable wire running to the fan. Splice the source neutral to the white cable wire and the ground to the ground wires. At the fan splice the wires, matching the colors of each.
To wire a 3-way switch circuit that controls both the fan and the light, use this diagram. As with all 3-way circuits, the common on one switch is connected to the hot source wire from the circuit. The common on the second 3-way switch is connected to the hot wires on the fan/light.