Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.
The source hot is spliced to the red wire which is connected to the bottom terminals on the switch at the other end. The black wire is connected to the top terminal on the switch which runs power back to the fan where it is spliced to both the black and blue fan wires.
In this wiring, the source is at the switch and 3-wire cable runs from there to the fan/light. The switch controls the light and the source is spliced through to the fan. With this arrangement, the fan is controlled by a pull-chain on the motor housing and the light is controlled with the switch. The neutral and ground wires are also spliced through to the fan/light.
Here GFCI’s are wired to a double-pole circuit breaker with the source split to provide 120 volts to two sets of receptacles. The neutral from the source is shared by both sets. Single-location protection is provided by each receptacle.
This diagram shows the wiring for multiple receptacles in an arrangement that connects each individually to the source. All wires are spliced to a pigtail which is connected to each device. This wiring allows for voltage at each device independent of the other outlets in the circuit.
In this arrangement a light fixture and exhaust fan are wired to the same source. The light is controlled with a single-pole switch and the fan controlled with a timer as in the previous drawing. The hot source is spliced to each controlling device and the output of the controllers are connected as in the previous diagrams on this page.
The hot wire to the fan in a fan/light kit will usually be black and the light wire will be blue. The white wire is usually the neutral which is always connected directly to the source neutral, either at the source or through a splice in the switch box. The white wire may also be used to carry current when necessary.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.
This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
This wiring diagram illustrates the connections for dual controls, a speed controller for the fan and a dimmer for the lights. The source is at the controllers and the input of each is spliced to the black source wire with a pigtail. From the controllers, 3-wire cable runs to the ceiling outlet box.
To wire an exhaust fan to a wall switch, use this diagram. These fans usually come with a small electrical connection box welded to the side of the housing. There will be a cover on the connection box that fastens with a small screw. Open it, pop the plug out of one of the wire holes and thread a wire clamp into it.
To wire a 3-way switch circuit that controls both the fan and the light, use this diagram. As with all 3-way circuits, the common on one switch is connected to the hot source wire from the circuit. The common on the second 3-way switch is connected to the hot wires on the fan/light.
The white wire is wrapped with black tape to identify it as hot. The black wire connects the fan to the speed controller. The red wire connects the light to the dimmer.
Here the exhaust fan is controlled by a timer instead of a switch. There should be two hot wires and a ground coming out of the timer casing, splice one of these to the hot source. Spice the second to the black, cable wire running to the fan. Splice the source neutral to the white cable wire and the ground to the ground wires. At the fan splice the wires, matching the colors of each.
This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.