Here the source is at the fan/light and a switch loop runs to the wall switch. The source is wired directly to the fan and spliced through to the switch. With this arrangement the light is controlled with the switch and the fan is hardwired for pull-chain control.
In this diagram multiple ground fault circuit interrupter receptacles are wired together using pigtails. Two-conductor cable is run between gfci’s, and the hot, neutral and ground wires from the source are spliced to the line terminals at each device. The load terminals are not used and each device provides its own, single-location protection.
Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.
Use this wiring when the source is at the fixture and you want to control the feed to both components with the same switch. Three-wire cable runs from the fan to the switch box and the source neutral is spliced to the white wire and to the fan neutral.