Here two receptacles in one box are wired using the device terminals. With this arrangement, if receptacle #1 fails, receptacle #2 may also fail if failure is due to physical damage. However, if the copper tab conductors between the terminals remain intact, even if #1 stops functioning, receptacle #2 will probably still work.
This diagram illustrates the wiring for a circuit with gfci receptacles followed by an unprotected light and switch. The light switch is connected directly to the source and the load terminals on the gfci are not used.
In this diagram, a light switch and receptacle are wired in the same box. Both devices are spliced to the same hot source and the neutral to the neutral on the receptacle, and through to the light fixture located in a separate box.
This diagram shows the wiring for multiple receptacles in an arrangement that connects each individually to the source. All wires are spliced to a pigtail which is connected to each device. This wiring allows for voltage at each device independent of the other outlets in the circuit.