Here two receptacles in one box are wired using the device terminals. With this arrangement, if receptacle #1 fails, receptacle #2 may also fail if failure is due to physical damage. However, if the copper tab conductors between the terminals remain intact, even if #1 stops functioning, receptacle #2 will probably still work.
In these cases, it should be wrapped with electrical tape to mark it as hot. The ground wires will be green and/or bare copper. The ground should be spliced with a short piece of wire and connected to each device and outlet box that has a grounding terminal. In these drawing the brass colored terminal represent the hot side of the device and the silver colored terminal represent the neutral. Ground wires and terminals are in green.
Here GFCI’s are wired to a double-pole circuit breaker with the source split to provide 120 volts to two sets of receptacles. The neutral from the source is shared by both sets. Single-location protection is provided by each receptacle.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.