This diagram is similar to the one above, but with the electrical source originating at the fixture. Three-wire cable runs from there to the controllers. The neutral wire from the source is spliced directly to the white wire on the fan/light. The hot source wire is spliced to the white on the 3-wire cable and then spliced to the input wires on both controllers at the other end.
Splice both the fan and the light hot wires together with the common wire from the SW2. The traveler wires are spliced together in the ceiling fixture box. To control the fan and light separately, a builtin switch such as a pull chain or remote control is required on the fan/light.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
Here one ground fault circuit interrupter protects multiple duplex receptacles coming after it, known as multiple-location protection. Two-wire cable runs from the gfci to all the following receptacles. The line terminals on the gfci are connected to the circuit source and the load terminals are connected with a pigtail splice to each of the following receptacles. This keeps each duplex connected directly to the gfci.