This page contains wiring diagrams for two outlets in one box. Included are arrangements for 2 receptacles in one box, a switch and receptacle outlet in one box, and 2 switches in the same box. In this diagram, two duplex receptacle outlets are wired using pigtails spliced to connect the terminals of each to the source wires.
This page contains wiring diagrams for ground fault circuit interrupter (gfci) receptacles. Included are diagrams for multiple gfci’s, a protected standard duplex receptacle, and a protected light fixture. Wiring for a switch and gfci receptacle in the same box is also shown to protect the switch and light or to protect other receptacles in the circuit. To wire a gfci circuit breaker see this link and wire a gfci switch combo at this link.
Use this wiring when the power source originates at the switch and you want to control both the fan and light from there. The hot source is connected directly to the bottom terminal on the switch. Two-wire cable runs from there to the ceiling fan.
Here the source is at the fan/light and a switch loop runs to the wall switch. The source is wired directly to the fan and spliced through to the switch. With this arrangement the light is controlled with the switch and the fan is hardwired for pull-chain control.
The hot source is spliced to the black, fan wire and the black wire running to the dimmer. At the other end, the black cable wire is spliced to one of the hot dimmer wires, it doesn’t matter which one. The other dimmer wire is spliced to the red wire in the switch box which is spliced to the blue, light wire at the other end.
Here the exhaust fan is controlled by a timer instead of a switch. There should be two hot wires and a ground coming out of the timer casing, splice one of these to the hot source. Spice the second to the black, cable wire running to the fan. Splice the source neutral to the white cable wire and the ground to the ground wires. At the fan splice the wires, matching the colors of each.
Here 3-wire cable is run from a double-pole circuit breaker and split to supply 120 volts to two sets of receptacles. The neutral wire from the circuit is shared by both. This wiring is commonly used in a 20amp kitchen circuit where two appliance feeds are needed, such as for a refrigerator and a microwave in the same location.
The black wire is splice to the output on the speed controller and to the black, fan wire at the other end. The red wire is spliced to the output on the dimmer and to the blue, light wire at the other end. The neutral from the source is spliced in the switch box with the white wire, and to the neutral wire on the ceiling fixture at the other end.